Question about AO Smith 1.5hp Pool Pump Motor 2 Speed Ao Smith Electric for Motor Pool & Spa Pump Bn34
Yes, it will handle the voltage...
It is odd indeed as a normal AOSmith two-speed motor will have quick-connect AND screw posts for line connection terminals. If you are certain there are only two screws yet the motor is a two-speed then the answer to the first question is yes; you'll need a female quick-connect terminal for your second line connection to the A terminal.
Posted on Apr 11, 2011
Testimonial: "Thanks. It's hooked up and working."
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get to try the service completely Free afterwhich it costs $6 per call and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: My pool originally had a
Is it going to run on 230V then? If so you would normally use red and black. The white wire should be a neutral and the ground wire is obviously ground.
Do you have a meter you can use to confirm the voltage between the wires? If you do you'll want to start with red and white since you seem to think black was not being used before. If the voltage reads 230 and the motor is set up for 230 then attach one wire to L1 and the other to L2...it will not matter which is connected where as long as one is on each terminal. Insulate the black and ground the ground lead to the motor ground screw.
If the voltage is not 230 between those two check between red and black. If that is the 230 then insulate white and put red and black to L1 and L2.
Posted on May 24, 2011
SOURCE: wiring a 230v ao smith
Hi, assuming you have 4-conductor wire, use the black and red wires for L1 and L2. It doesn't matter which goes to which. If you do not have a red wire, use black and white. The green or bare wire in a 3-wire cable goes to the ground. If you have 4-conductor wire, the ground wire is the one you used for the GFCI on the breaker--usually the white wire. Please let me know if you have more questions, and thanks for using FixYa.
Posted on Aug 08, 2011
Tips for a great answer:
Nov 30, 2013 | AO Smith Pool Pump Motor Hayward Swimming...
Apr 13, 2013 | AO Smith 1.5hp Pool Pump Motor 2 Speed Ao...
Oct 23, 2012 | Pool & Spa
Dec 06, 2011 | AO Smith 1.5hp Pool Pump Motor 2 Speed Ao...
Aug 17, 2010 | Refrigerators
Jul 31, 2010 | AO Smith A O Smith Motors Century 1hp 115v...
Jul 19, 2010 | AO Smith 1.5hp Pool Pump Motor 2 Speed Ao...
Oct 22, 2009 | AO Smith A O Smith Motors Century 1hp 115v...
Sep 25, 2009 | AO Smith 1.5hp Pool Pump Motor 2 Speed Ao...
Jan 13, 2013 | AO Smith 1.5hp Pool Pump Motor 2 Speed Ao...
722 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: