Question about Heating & Cooling
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
SOURCE: COMPRESSOR NOT RUNNING, HOT
The high side/low side pressure equalization you describe is normal for a compressor sitting idle.
If you have an ohm meter you can check the compressor windings for opens and shorts. If your compressor is 3 phase as you state (this would be very unusual for a residential unit) you should have continuity across all 3 phases and no continuity to ground. Take the compressor out of the circuit before you check.
If the compressor does have crankcase heat, it should have been left on for at least 24 hours before starting the unit. Another cause for failure could be overcharging which could have resulted in refrigerant slugging back to the compressor.
Does the unit have any low or high pressure control safeties? If so, check them too - some have resets. You said the condenser fan ran so it's not likely the breaker blew, but check anyway and also check to make sure you have available power on all 3 phases.
Posted on May 03, 2009
Tips for a great answer:
Jul 26, 2017 | Refrigerators
Mar 17, 2015 | Carrier FB4ANF060 HVAC Electric Unit & AC...
Dec 06, 2014 | Air Tools & Compressors
Sep 04, 2014 | Heating & Cooling
Jun 25, 2014 | Goodman CKL24AR24 Air Conditioner
Jun 24, 2014 | Ingersoll Rand Stationary Air Cooled...
Mar 11, 2014 | Air Tools & Compressors
Sep 20, 2011 | Ingersoll Air Tools & Compressors
193 people viewed this question
Usually answered in minutes!