Question about Computers & Internet
Need to notify the camper manufacturer or an rv shop because most camper / rv are not cookie cutter designs -[ multi options ]
Posted on Jun 24, 2017
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
I am an electrician. You must measure the voltage across the black and red wires. Measuring each wire to the neutral will not cut it. If both your red and black wire are on the same phase the heater will not work.
To double check your wiring, measure the voltage across the two screws feeding your subpanel, they should be 240v or 208v depending on your power company. Then do the same at the breaker feeding your thermostat. Again it should read 240v.
If you have no potential across the screws it is possible that you installed an incorrect breaker. Not all breakers with two screws on them are 240v breakers. There is what is called a twin or split breaker that has two screws that are on the same phase. These are for wiring two 110v circuits, when you run out of spaces in the panel.
Double check everything. This is a relatively easy circuit to wire, even for homeowners. If the heater does not work them something is wrong so do not leave the circuit energized.
Posted on Mar 16, 2009
you need to find the propane lines and where ever you have a joint you need to put "snoop" on it. which is basicly soap and water sorry my spelling sucks. anyway you do this with the propane on and whereever you have bubbles you have troubles. you can even check your lines with it. Now yoiur electrical woes can be fixed by tracing your wiring and finding out where you have a short this is when two wires are either touching eachother both of these problems take time and they take some experience. If you mess this up you could blow yourself up. Let me know what you are going to do. I'm worried for you
Posted on Jul 04, 2009
SOURCE: 15 AMP versus 20 AMP outlet plug
The circuit is protected by the 15 amp breaker. That's what matters, the wire size and the breaker feeding it. It's OK to have a 20 amp recepticle fed by a 15 amp breaker.
Posted on Sep 11, 2009
Testimonial: "Concise answer"
Tips for a great answer:
Mar 02, 2015 | Microwave Ovens
Jan 06, 2014 | 2004 Jeep Liberty
Apr 18, 2011 | Dometic Refrigerators
Jan 31, 2011 | Electronics - Others
Jan 14, 2018 | Roper RT18HDXKQ Top Freezer Refrigerator
Mar 12, 2010 | 2003 Chevrolet Silverado 2500HD
May 17, 2009 | 1987 Chevrolet Camaro
Apr 30, 2009 | Rv Motorhome Dual Co & Lp Gas Alarm...
Nov 26, 2008 | Coleman 5640B807 Compact Refrigerator
133 people viewed this question
Usually answered in minutes!