Question about Sharp Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
This is a single speed permanent split capacitor motor for the condenser. One of the capacitor wires shows infinite resistance to hot and netral. The motor needs to be replaced.
Posted on Mar 31, 2009
try draining the water. Mine did the same thing. Started right back up. There is alot of water be careful.
Posted on Aug 03, 2009
If the a/c fails to continue to blow cold there could be a few problems you can look for. First once you activate the system check to see if the compressor kicks in. You will hear the compressor humming . Once the a/c quits cooling go and see if the compressor is still running. If its not running its probibly gone into thermal overload (compressor overheated). If that is the case then you need to check to see if the coils are icing up if they are icing up then the problem is with 1) air flow restriction filter dirty, coils dirty simple repairs there replace filter, clean evaporator coil with a coil cleaner that can be purchased at a home repair store cleaning the condensor coil the same. 2) system is low on freon in which case the system will need to be recharged. Also, If you have a digital thermostat replace the batteries that may also be of some help. Good Luck on repairs
Posted on Aug 31, 2009
insufficient cooling have several reason,most common factor is low freon charging due to service factor,defective thermostat control,dirty evaporator and condenser fin,try to check the current rating using ammeter clamp tester if the rated current read in tester below the rated current on tag(compressor)
you need to charge freon,if the fin and evaporator is dirty need to ve clean,if the thermostat is not functioning replace thermostat.
also consider the main defective if the aircon is running chck the compressor if it is running by touching the tip of screw driver to the top body of compressor you can feeel vibration,if compressor is not running yo don't have cooling effect only blowing of air.on repairing this this should be done by a certified aircon technician,have a nice day fix my rate,thank you very much.
Posted on May 14, 2010
The unit is overheating and tripping the internal overload of the compressor. Clean outdoor coils.....check outdoor fan to see if it turns or is siezed......possible bad Start/Run Capacitor which is a very common failure on condensing units......possible bad fan motor need replaced! Unit compressor can be cooled with a water hose to get it to reset the internal biometalic high limit switch that is located in the hermetically sealed compressor!
Posted on Aug 22, 2010
Tips for a great answer:
Jul 23, 2016 | Danby Heating & Cooling
Oct 04, 2014 | Heating & Cooling
Jul 19, 2013 | Sharp Cv-p12lx 11500 Btu Portable Air...
Jun 12, 2011 | Haier CPN12XH9 Portable Air Conditioner
Aug 06, 2010 | Carrier 36KCARMS Air Conditioner
Jul 17, 2010 | Whirlpool ACP102PS Portable Air...
May 27, 2010 | Danby DPAC8020 Air Conditioner
Apr 02, 2010 | Sharp CV-P09FX Air Conditioner
63 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: