Question about Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
On the unit outside there is a button that says "push man. pull auto" if it is set to push man then the fan will go constantly.
Posted on Nov 08, 2009
test thermosat for proper operation ie-broken wire-power if good jump stat and check if unit goes on if it does than stat internal problem or wiring problem and needs replacement or repair --if stat good check fan safety/high limit sensor if good would need to check and test thermocouple thats the tube that the pilot flame burns on may be enough to keep pilot burning but not enough to open valve for heat demand
Posted on May 31, 2010
SOURCE: Pilot lights up but would
This is the proper cycle of a furnace and what should happen.
Inducer motor kicks on, it runs for a little bit, about 3-5 seconds, then you should see a bright yellow glow, this is the igniter, shortly after, you should hear a click and the gas should start to flow, almost immediately it turns to a blue flame. Then your igniter should turn off and the blower motor start up.
If the pilot turns on and the gas ignites, then shortly after the unit shuts off, chances are this is your blower motor. It is not starting up, then the heat limit is reached in your unit and the safety shuts it off.
Posted on Mar 02, 2011
Tips for a great answer:
May 26, 2014 | Heating & Cooling
Apr 04, 2014 | Jandy Lite2 LJ125 Ceramic Gas Heater
Jun 14, 2012 | Heating & Cooling
May 31, 2010 | Heating & Cooling
Feb 25, 2010 | Heating & Cooling
Sep 22, 2009 | Heating & Cooling
Jun 11, 2009 | Heating & Cooling
Apr 26, 2009 | Heating & Cooling
Sep 20, 2017 | Heating & Cooling
41 people viewed this question
Usually answered in minutes!