Question about Heating & Cooling
I'm guessing you have an oil burner because of the "Adequate Fuel" statement. If so, be VERY careful while following this suggestion, OK? There should be a small inspection hatch on the front above the burner. Be sure everything is turned off and the fire is NOT still burning in the combustion chamber. Use a flash light and look in the inspection hole. If you can't see the end of the burner, use a mirror. If there is oil sitting in the bottom of the chamber, don't fire it. If you can see the end of the burner, it will look something like the picture. What usually happens is the nozzle partially plugs and the spray pattern goes a little goofy. As a result, the oil does not burn completely. Some will build up on the bottom of the chamber, some will create a lot of smoke and some will harden on or around the electrodes. All you can really do is check for unburned oil in the chamber and see if the electrodes are shorted with carbon. If you see a carbon arch on the electrodes, you can VERY gently remove it for a quick fix. If a lot of oil has built up in the chamber, the fire will continue to burn when the thermostat is satisfied and shuts off the burner. I have seen flu pipes red hot from this so be careful in deciding to re-fire it. There are several CRITICAL adjustments that require special tools to accomplish. Regardless of how things work out, you need a service tech. who knows what he is doing. BE CAREFUL! Sorry, my picture is too large. Just go slow and look it all over. If you are not in an emergency situation, call a service guy.
Posted on Apr 01, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 17, 2014 | Heating & Cooling
May 29, 2013 | Heating & Cooling
Feb 17, 2013 | Cars & Trucks
Feb 17, 2013 | Chevrolet S 10 Cars & Trucks
Sep 09, 2012 | Nissan Cars & Trucks
Dec 05, 2010 | Goodman GPG152407041 15 SEER Packaged...
Jan 05, 2010 | Goodman Heating & Cooling
Dec 31, 2009 | 1997 Ford F150 Regular Cab
Nov 15, 2008 | Kitchen Appliances - Others
Oct 18, 2017 | Heating & Cooling
67 people viewed this question
Usually answered in minutes!