Question about Honeywell Heating & Cooling
I'm doing a lot of guessing here for lack of information. You have a residential boiler and hydronic heating system that is zoned around your home and each zone has an independent thermostat?
Again, I need to guess. The old valve was spring return with yellow, blue and red wires? If all is true so far, then I think you had a single end switch with one COMMON - one NORMALLY OPEN and one NORMALLY CLOSED contact. 6 wires would make up 2 end switches. Brown is a normal color for one lead of an end switch. If this is all true, your new switches are probably NORMALLY OPEN and you only need 1. If this did not help you, give me a better description of old and new and I will get this correctly answered for you.
Posted on Apr 01, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 21, 2017 | Heating & Cooling
Jan 18, 2011 | Honeywell Heating & Cooling
Dec 14, 2010 | Honeywell Heating & Cooling
Feb 08, 2010 | Honeywell Electronic Programmable...
Jan 30, 2010 | Honeywell Electronic Programmable...
May 10, 2009 | Honeywell Programmable Thermostat Heater
Dec 07, 2008 | Heating & Cooling
May 01, 2008 | Honeywell Electronic Programmable...
265 people viewed this question
Usually answered in minutes!