Question about Jandy AQUALINK RS TELELINK KIT
The circuit breaker likely has a ground-fault interrupter which is triggered by any current leaking to ground in the system. Resetting the breaker will cause it to be immediately triggered open again by the ground fault. You will need to isolate where the fault lies starting by disconnecting at the point closest to the breaker, checking for the presence of AC voltage at that point when the breaker is reset, then adding another segment and checking for AC voltage at the added segment. When you add the segment with the problem, you will find that resetting the breaker will cause it to trip again. If as you say that the bulb was fine but the light was broken, this would be a likely location for the ground fault as it was the only disturbance (you replaced the bulb with a new which also didn't work since the socket was broken) made to the system before turning the power back on (to the light) thereby causing the pump/filter to stop working (circuit breaker had just been tripped by the turning on of the light switch thus removing AC power to the entire system).
Posted on Apr 01, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get 2 Free calls (no credit card required) and instant help on almost anything you can think of (from cars to computers, appliances, handyman, and even pets).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 03, 2016 | Jandy Pool & Spa
Apr 10, 2014 | Jandy Aqualink Rs4 One Touch Control...
Oct 06, 2013 | Standard Power Center for Aqualink Rs
Mar 27, 2013 | Jandy PDA-PS8 Aqualink RS PDA PS8 Wireless...
Nov 22, 2011 | Jandy AquaLink RS OneTouch RS8 Pool or Spa...
Feb 23, 2011 | Jandy Aqualink - Rs24 One Touch Pool / Spa...
Oct 10, 2009 | Jandy Aqualink Rs4 One Touch Control...
System locked up. Handheld
is frozen at WAITING screen. Microprocessor
Here is what you do:
power to the system.
battery at the Power Center and turn on power.
Reconnect the battery and reset time and date.
You are welcome... BadWally sends.
Jul 03, 2009 | Jandy AQUALINK RS TELELINK KIT
274 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: