Question about Heating & Cooling
I would first eliminate one furnace from the equation, the exterior wood furnace... turn its tstat down. Will the gas furnace then operate normally? Can you run the blower manually, as in summer mode? Make sure your filters are clean also... that can sometimes overload the blower.
Posted on Apr 12, 2017
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: goodman gmp075-3
I am confident the technician(s) have done this but check anyway.
Gas pressure 4-7 inches W.C for natural, 10 - 11 for Propane.
Air filter clean and unrestricted.
Temperature over supply plenum 140 degrees F.
All registers open and unrestricted.
Vent and intake unrestricted and not blocked.
Condensate hoses free of debris and draining.
OK now lets check to see if the furnace is staying on long enough.When it runs for a heat cycle, is the flame staying on until about 2 minutes prior to achieving the set temperature or is it cycling everyfew seconds and never reaching temp? To check you will need to view the flame through a small viewing port of thru the fins in the front door. Watch them for 10 to 15 minutes.
If they are staying on a long time, we will need to see if the room blower is working properly. If they are going out quickly and or cycling. Get the technician on the pone to talk it over. It could be a safety sensor.
If the blower stays on and the burners are on as well, you have a door open somewhere. Just kidding. Remove the thermostst documenting which wires go where. Take the white wire and cross it with the red wire. This will (or should) turn on the furnace. Clamp them together untill the either the house gets warm or you are confident it is not going to reach temperature. If it did get close to the temperature you wanted, it is a thermostat issue. If not, you got me!
And they say we have an easy job! Get beck to us with your results.
Posted on Jan 23, 2008
Hi!!! You might have a bad flame sensor its a single rod located in the burners its white..If the unit runs and then shuts off and on and off.change your flame sensor..Good luckk..
Posted on Jan 04, 2009
It sounds like you may have issues with the furnace. A qualified professional can go over the system and the house to let you know if the system and unit are properly sized. The poor performance of a furnace can be a sign of carbon buildup in the furnace.
Good luck, hope this helps.
Posted on Jan 10, 2009
SOURCE: Heater blower problem
under the hood of the car on the passenger side you will see a round motor sticking up.thats the blower motor there should be 3 screws holding it in place and one plug to unplug.you lift the old motor out and put the new one in in its place
Posted on Jan 13, 2009
Tips for a great answer:
on Jan 08, 2011 | Heating & Cooling
Feb 05, 2011 | Heating & Cooling
Jan 17, 2011 | Heating & Cooling
Oct 26, 2009 | Intertherm P3RA-036K Air Conditioner
Oct 05, 2009 | Weather King 10AJA3601AH Air Conditioner
Oct 03, 2009 | Samsung Heating & Cooling
Feb 21, 2009 | Aprilaire 600 Humidifier
Feb 11, 2009 | Ruud Central System Air Conditioner
39 people viewed this question
Usually answered in minutes!