Question about Heating & Cooling
Disconnect the black power wire where it is connected to the furnace with breaker off. Put a wire nut on it and then turn the breaker on. If it continues to trip, the problem is not the furnace and you will have to trace the power wire back to the breaker box to find problem. Next, disconnect the black wire from the breaker (with breaker off) and then snap breaker on. If it trips, bad breaker. If the furnace was disconnected and breaker did not trip, you have a short either on the P C Board or the transformer.
Posted on Mar 31, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 04, 2012 | Bryant Westinghouse Bqc Quad Circuit...
Jun 10, 2012 | Goodman Heating & Cooling
Jul 18, 2011 | Heating & Cooling
Mar 31, 2011 | Heating & Cooling
Jul 19, 2010 | Challenger Connecticut Electric UBITB-A230...
May 24, 2010 | Heating & Cooling
Jan 07, 2010 | Heating & Cooling
Dec 07, 2009 | Refrigerators
Jan 09, 2009 | Electric Circuit Breaker Kit for Furnace
436 people viewed this question
Usually answered in minutes!