Question about GE Hammering
I also had this problem and was eventually able to get the following information from GE.
1. Shut off power to the panel (I have to state the obvious).
2. Install a double pole breaker in slots 1 and 3.
3. Locate the small plastic peg between the two main power lugs. My terminology may be wrong, but this is where you would feed power if not backfeeding.
4. The hole on the 90 degree tab of the retainer then fits over the plastic peg. Orient the retainer so the upside-down "J" portion fits over the breaker lip.
5. Press a lock washer over the plastic peg. This holds the retainer in place.
6. Feed your cable into the breaker and tighten.
7. Label main power shutoff as required by code.
8. Power on.
Posted on Oct 13, 2011
These breaker holders are not the tight fit one might think,the manufactures only provide these things for code,you prob have it in correctly
Posted on Jun 13, 2011
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 19, 2017 | GE Electrical Supplies
Feb 21, 2013 | Bryant /murray Bj2200 Main Circuit Breaker...
Feb 27, 2012 | General Electric GE 125 Amp Indoor Main...
Feb 18, 2011 | Cutler Hammer 100 Amp Main Breaker...
Dec 11, 2010 | Cutler Hammer 100 Amp Main Breaker...
Oct 03, 2010 | Siemens 100 Amp Main Breaker Renovation...
Sep 10, 2010 | General Electric GE ELECTRICAL TQD22200X2...
Jan 24, 2010 | Cutler Hammer 125 Amp Main Lug Indoor Load...
Aug 24, 2009 | Electrical Supplies
Jul 23, 2009 | Goodman CLQ36AR49 Air Conditioner
712 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: