Question about Heating & Cooling
I understand that you are having a problem with your Rudd condensor. The fan is turning slowly and the compressor is making a buzzing noise which has a Diversitech hard start conected to the capcitor.
You have already replaced the run capcitory on the unit and have attached the compressor wire to therm and c and the fan to therm and fan. The hard start kit shoudl be attached to the therm and c with your compressor wires attached to the same place. The hard start kit is to give the compressor the extra push (electrical charge) to start.
You need to check your connections and make sure that you purchased the proper run capcitor. If you have purchased the proper compacitor and the connections are right then you have a bad fan and the compressor as gone out on the unit.
Thank you for choosing FixYa.com
Posted on Mar 28, 2011
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Aug 29, 2013 | Ruud Heating & Cooling
Jul 27, 2012 | Ruud UAMB Air Conditioner
Jul 26, 2011 | Ruud UBHC Air Conditioner
Aug 13, 2010 | Ruud UBHC Air Conditioner
Jun 27, 2010 | Ruud UAKA037 Air Conditioner
Aug 10, 2009 | Ruud UAKA037 Air Conditioner
Jun 30, 2009 | Ruud UAMB Air Conditioner
Jun 27, 2009 | Ruud UAMB Air Conditioner
Apr 11, 2009 | Goodman CKL24AR24 Air Conditioner
May 28, 2008 | Ruud Matching Split Air Conditioner
135 people viewed this question
Usually answered in minutes!