Question about Intertherm Heating & Cooling
Yes there are somethings you can check your self...
On the first one...you are getting power to the board but the board thinks that the hot (L1) and the neutral (N) are reversed or there is not a good ground to the furnace...Use an electrical meter to make sure that the black wire is the "hot" wire and that it goes through the switch and is hooked to the L1 terminal of the board...also make sure that your furnace is properly grounded and also that the electrical panel is grounded properly...this is very important..the L1 does not mean limit... it is referring to the terminal on the main board...
Check page 38 of this for the wire schematic and the note for the five flashes there...
On the second one... the furnace is not staying lit because it is not proving that you have ignition...
It could be a bad ground issue also...check that the flame is hitting the ignitor when it lights...the ignitor is also the flame sensor...if the burner ground is bad to the board it will not sense the ignition...a bad furnace ground will also do that...
Also a bad ignito or a very dirty ignitor can also cause that problem...be very careful if trying to clean the ignitor as they are very fragile and can break easily...
I sounds very possible that you have a bad grounding problem and that is the cuase of both problems...they are just reacting to it differently... did both problems crop up at the same time???
Comment back with any questions...
Posted on Mar 26, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 30, 2015 | Heating & Cooling
Jul 18, 2014 | Amana PTH093B35AJ 9100 BTU ThruWallWindow...
Jan 30, 2014 | Intertherm 56000 Btu Gas Furnace
Oct 26, 2013 | Intertherm 56000 Btu Gas Furnace
Oct 20, 2011 | Intertherm P3RA-048K Air Conditioner
Jul 18, 2011 | Water Heaters
Mar 05, 2011 | Honeywell Heating & Cooling
Jan 30, 2011 | Heating & Cooling
Oct 23, 2010 | Dishwashers
May 04, 2017 | Heating & Cooling
210 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: