Question about Mitsubishi MSZ-A24NA Split System Air Conditioner
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Without seeing the unit,
1 - the condenser fan (which is in the outdoor unit) could be blown. This would cause the unit to go off on high head pressure.
2 - it could be low on refrigerant, which makes it do nothing but blow room temperature air around. The unit would go off on low pressure
3 - the filter is dirty, blocking the cooling
4 - the compressor could be shorted, or a corroded wire somewhere that feeds the contactor
Mr. Slim Ductless Splits are the best on the market and should only be repaired by a trained technician.
Hope this helps.
Posted on Jul 23, 2010
SOURCE: When unit is turned on
It's communication error between indoor and out door unit.
Comms Error, check your wiring, remove external pumps. Split/Multi - check volts from terminal N to 3 = 0 - 65 Vdc, Multi V - 4 Vdc terminals 3 and 4
Posted on Jan 06, 2011
SOURCE: Our heat pump is blowing
Below is a quick breakdown of the BTU's. One as you can see is at 65 degrees and the other is for 17 degrees. The BTU's are more than cut in half at 17 degrees as you can see. Your heat pump will struggle at the lower temperatures.
Outdoor Heating Air Compressor Air Capacity Flow Current (deg °F) (BTUH) 65 23,529 17 11,200
Posted on Jan 24, 2011
Tips for a great answer:
Jun 08, 2017 | Measuring Tools & Sensors
Jan 07, 2016 | Sanyo 24KS72 Split System Air Conditioner
Nov 30, 2014 | Heating & Cooling
Jun 06, 2014 | Heating & Cooling
Mar 18, 2014 | Fujitsu Heating & Cooling
Feb 23, 2014 | ComfortStar CHH012CD-13B Wall Mounted Mini...
Jan 13, 2011 | Mitsubishi MS24WN Air Conditioner
May 23, 2010 | Goodman CKL24AR24 Air Conditioner
Mar 05, 2009 | Goodman GPC1342H21A Air Conditioner
May 24, 2017 | Refrigerators
70 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: