Question about Rheem Water Heaters
1) If upper element is receiving 240V, then water heater should have some hot water.
If upper element is burned out, then tank will have no hot water, but element will still test for 240V
2) Keep in mind that upper element heats top part of tank first.
Only when top part of tank reaches thermostatic temperature will power be sent to lower thermostat and element. This is called non-simultaneous operation.
3) Non-simultaneous operation is necessary for most water heater installations because both elements are not ON at same time. Either upper element is ON or lower element is ON or both are off.
Each element is typically 4500 watts, which is 18.75 amps.
If both elements were ON at same time, it would consume 37.5 amps, so circuit breaker would have to be 40 or 50 amp with 8 or 6 gauge wire.
4) Add a comment with your experience so others with same-similar problem can benefit.
Also take advantage of fixya expert assistance live.
For a price, expert works with you while you work on water heater or any do-it-yourself project.
Fixya is always less expensive than a service call.
Posted on Mar 26, 2011
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Mar 14, 2015 | Reliance 50 Gal. Electric Water Heater...
Sep 09, 2014 | Water Heaters
Apr 28, 2017 | Water Heaters
Feb 09, 2013 | Water Heaters
Oct 02, 2012 | Water Heaters
Mar 20, 2011 | Rheem Water Heaters
Dec 07, 2010 | General Electric GE SmartWater Household...
Nov 09, 2010 | RELIANCE ELECTRIC WATER HEATER
Nov 04, 2010 | Rheem 40 GAL ELEC TALL Water Heater 6YR SC...
Nov 15, 2008 | Water Heaters
186 people viewed this question
Usually answered in minutes!