Question about Heating & Cooling
If the pressure switch is open, that means that the inducer is not moving enough air to close it, the pressure switch is bad, or the heat exchanger may be cracked.
Check for air flow...go outside and see if air is coming out the vent pipe....make sure there is no water built up inside the vent pipe.
Make sure the air intake pipe is ope and not clogged if you have a two pipe system...
Check the small hoses by the furnace for cracks or water in the hoses...
Check for condensate buildup inside the heat exchanger...
A cracked heat exchanger can also cause a lack of pressure and or pressure differential....
If everything else checks out then you may have a bad pressure switch... they DO go bad...
Here is a tip that will help you try to figure out why yourfurnace is not working.
BasicFurnace or Heating System Troubleshooting
Posted on Mar 24, 2011
Testimonial: "It was a bad circut board. "
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jan 02, 2016 | FACTORY AC PARTS Limit Switch Double Pole...
on Dec 20, 2009 | Heating & Cooling
Sep 21, 2014 | Heating & Cooling
Mar 08, 2013 | Heating & Cooling
Dec 12, 2009 | Heating & Cooling
Oct 16, 2009 | Heating & Cooling
Oct 12, 2009 | Heating & Cooling
Mar 05, 2009 | Weather King 12AJA4801AH Air Conditioner
Mar 04, 2009 | Goodman GMS90703BXA Heater
Jan 26, 2009 | Kitchen Appliances - Others
318 people viewed this question
Usually answered in minutes!