Question about Goodman Heating & Cooling
Marc, look for where the gas line enters the furnace and remove the panel adjacent to it. That should gibe you access to the pilot light. Also, look for a pilot access door, near where the gas line enters the furnace. The gas line will either be 1/2" flexible copper tubing. 1/2" black iron pine or 1/2" vinyl coated flexible stainless steel. Look for the lighting instructions inside or on the side of the unit.
Hope this helps you solve the problem.
Posted on Mar 24, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 14, 2016 | Intertherm Heating & Cooling
Jan 24, 2016 | Goodman Heating & Cooling
Sep 30, 2013 | Whirlpool Water Heaters
Jul 28, 2011 | American Standard 40 G Natural Gas Water...
Oct 27, 2009 | Heating & Cooling
Sep 22, 2009 | Carrier Heating & Cooling
Aug 27, 2009 | Ruud UAMB Air Conditioner
182 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: