Question about Heating & Cooling
Before you buy a new condensor fan motor check the contacts to the motor are not worn or pitted.
Hold or push the contactor in by using an insulated screwdriver and see if the fan motor turns.
Also the start cap you bought? was it the correct one meaning mfd micrfarad?
If all the above checks out ok then you need a fan motor,you can wire the motor direct to check it also.
From what you describe it sounds like the fan motor is burnt up and worn out,not uncommon.
Posted on Mar 22, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 06, 2012 | Ruud UBHC Air Conditioner
Aug 25, 2011 | Ruud UAMB Air Conditioner
Mar 27, 2011 | Heating & Cooling
Aug 20, 2010 | Amana Heating & Cooling
Jul 19, 2010 | Goodman CLQ36AR49 Air Conditioner
Dec 08, 2009 | Goodman CPLE24-1 Air Conditioner
May 18, 2009 | Heating & Cooling
May 02, 2009 | Goodman CLQ36AR49 Air Conditioner
97 people viewed this question
Usually answered in minutes!