Question about Heating & Cooling
It would really help to know who the Manufacturer of your furnace is and the Model Number.
Posted on Mar 21, 2011
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Dec 22, 2015 | Coleman Heating & Cooling
Apr 23, 2011 | Heating & Cooling
Dec 27, 2010 | Heating & Cooling
You need to find out if the problem is in the T-stat, T-stat wire or in the furnace you can do this in a few easy steps
Step 1- Unwire the low voltage from the furnace. Then turn the power back on and see if the blower comes on if it does then the problem is in the furnace and you will need to troubleshoot the furnace (see bottom of page for troubleshooting furnace) if it does not then proceed to step 2
Step 2- Wire the low voltage back up to the furnace (follow the wiring diagram below). And unwire the T-stat, make sure that no wires are touching each other, then turn the power back on to the furnace, if the blower starts then you have a short in the T-stat wire and you will need to pull a new wire. If it does not then proceed to step 3
Step 3- Turn the power back off at the furnace and wire the T-stat back up (follow the wiring diagram below). Turn the T-stat to auto heat 90 if the heat does not start but the blower just runs then you need to replace the T-stat.
Nov 24, 2010 | Comfort-Aire Heating & Cooling
Oct 29, 2009 | Cross Furnace Draft Inducer Blower 115...
May 03, 2009 | Carrier Heating & Cooling
Feb 21, 2009 | Heating & Cooling
51 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: