Question about Honeywell Heating & Cooling
What i'm reading into this is your pilot may need to be cleaned.when you say bigger is it "lazy"also maybe some yellow to it? the pilot should be sharp and blue.to clean the pilot you need to remove it from the burner.a 7/16 is the normal size nut to the tubing.remove the tubing from the bottom of the pilot and there should be a little thimble looking thing that will drop out.there is a very small hole in it. do not enlarge the hole but clean it and reassemble. hope that works for ya.
Posted on Mar 23, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 03, 2014 | Emerson Lennox Ducane Armstrong Furnace...
Mar 01, 2013 | Lennox Heating & Cooling
Nov 19, 2012 | Heating & Cooling
Mar 23, 2011 | Heating & Cooling
Jan 04, 2011 | Honeywell Heating & Cooling
Oct 16, 2009 | Honeywell Electronic Programmable...
Jan 13, 2009 | Honeywell Electronic Programmable...
44 people viewed this question
Usually answered in minutes!