Question about Heating & Cooling
Check to see if your getting 24v between red and com.if you got 24v there then you have a bad t-stat
Posted on Aug 03, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 01, 2012 | Frigidaire Heating & Cooling
Jun 06, 2008 | Sharp Heating & Cooling
Aug 08, 2011 | Heating & Cooling
Feb 04, 2011 | Heating & Cooling
Nov 10, 2010 | Heating & Cooling
Aug 06, 2009 | Heating & Cooling
Apr 11, 2009 | Goodman CKL24AR24 Air Conditioner
Jan 14, 2009 | Dometic Heating & Cooling
Dec 10, 2008 | Heating & Cooling
Dec 30, 2007 | Heating & Cooling
62 people viewed this question
Usually answered in minutes!