Question about Garden
Thank you for posting your question here on Fixya.com. If this answer does not fix your problem, please comment with additional details prior to rating the answer. Positive feedback is appreciated once your problem is solved!
For starters you will need to proceed carefully...the noise you hear is water beginning to boil within the heat exchanger. The pressure that results can cause the unit to rupture or worse, blow. DO NOT ALLOW THE HEATER TO OPERATE IN THIS CONDITION FOR MORE THAN A MOMENT OR TWO as you attempt to repair it.
Water boils in a heater due to low flow, allowing the water to get too hot as it passes thru, or a faulty part or parts within the unit. We'll start with parts:
The bypass valve inside the header may be the issue if it is stuck closed. You will also want to inspect the thermostatic control valve in the header (if one is present) and inspect the overall condition of the heat exchanger. It is likely aggressive water has damaged some or all of these parts causing the banging noise you hear.
Your manual might also be helpful... http://www.pentairpool.com/pdfs/MaxEThermOM.pdf
If the heater checks out then flow is the likely cause. It is possible there is an issue with the pump and/or filter not getting enough flow thru the heater. Check the overall system flow. If it is reduced too low the water inside the heater gets too hot and begins to boil causing the noise you here. Speeding the flow back up will eliminate the issue. Check all the trap baskets and the filter for debris and clean up what you find; backwash a sand filter or clean a cartridge or DE unit. If your pressure gauge is broke replace it and check system pressure. If it is low again that is a sign of a flow problem. If flow is low and all these items check out open up the pump and inspect the impeller for clogged vanes or a blocked inlet eye.
Thank you for posting your question here on Fixya.com.
If this answer does not fix your problem, please comment with additional details prior to rating the answer. Positive feedback is appreciated once your problem is solved!
Posted on Mar 21, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 26, 2010 | Sta Rite SR400NA Max E Therm Pool Spa...
Sep 19, 2010 | Sta Rite Sr400na Max E Therm Pool & Spa...
Aug 07, 2010 | Hayward Gas Swimming Pool Heater 100k Btu...
May 18, 2010 | Sta Rite Sr400na Max E Therm Pool & Spa...
May 08, 2010 | Sta Rite Sr400na Max E Therm Pool & Spa...
Jan 25, 2009 | Harmsco Pool and Spa Cartridge for Filter...
99 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: