Question about Honeywell Heating & Cooling
To replace it, you'll need to know whether it's a Robertshaw or Maxitrol Valve. As well as the Model number of the valve and whether it's Natural Gas or Propane Gas. Unless, you're really experienced with working on gas appliances, I would not recommend this as a DIY project.
Hope this helps solve your problem.
Posted on Mar 21, 2011
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
on Feb 25, 2011 | Water Heaters
Jul 31, 2012 | Heating & Cooling
Apr 24, 2011 | Rheem RTG-74PVN-2 Natural Gas Pronto Whole...
Feb 23, 2011 | RELIANCE ELECTRIC WATER HEATER
PROBLEM #1 - HOT SURFACE IGNITOR DOES NOT GLOW RED
(Remember to wait for purge time, 17/34 seconds, on models so equipped).
A. No main power
B. Faulty transformer
C. Faulty thermostat
D. Faulty limit switch
E. Faulty blower interlock switch
F. Faulty hot surface ignitor
G. Faulty ignition control
Perform normal system checks of main power, transformer, thermostat, limit
switch, blower interlock switch, and replace faulty component.
With power on and thermostat set at its highest position, check voltage
between "TH" and "TR" on HS780 ignition control. If 24 volts is not present
check output at transformer. If no, replace transformer. If transformer
checks out OK look at other controls in the 24 volt circuit I.E.: thermostat,
limit switch, blower interlock switch. Check for 120 volts between "neut"
(L2) and "120" (L1). Check for 120 volts at the ignitor across "IGN" and
"IGN" terminals on the HS780 ignition module. If 120 volts is present,
replace ignitor. If no, replace the 780 series module
PROBLEM #2 - IGNITOR GLOWS RED BUT MAIN BURNER
A. Improper ignitor alignment
B. Faulty ignition control
C. Faulty gas valve
D. High inlet gas pressure
E. Polarity reversed
F. No earth ground
Check for availability of gas at gas valve. Make sure the manual valve
upstream of the gas valve and the gas valve are in the full on position. Also
make sure gas is being supplied to the system at the proper pressure, too
high will lock-up the valve.
Check proper polarity of "NEUT" and "120" on the ignition control by reversing
the wires, if reversed gas valve will not open. If this does not solve the
problem, replace wires as they were.
Check for proper ignitor position.
Check for a good earth ground by using a meter connected between L1
and furnace chassis. Should read 120 volts, if no, check and/or repair ignition
ground wire or ignition control mounting screws.
CAUTION POLARITY MUST BE OBSERVED
Check for 24 volts at the gas valve terminals; "1" and "2" on a 7200 series,
"M" and "C" on a 7100 series, "TH" and "TR" on a 7000 series. If yes,
check wire integrity or change the gas valve. If no, change the 780 series
That is pretty much all of the troubleshooting required.
Thanks for choosing FixYa,
Feb 14, 2011 | Rheem 40 Gallon FVR NATGAS Low WATER...
Jul 09, 2010 | Rinnai Digital Remote Water Heater Control...
Mar 12, 2010 | RTO Atwood DSI-RV Water Heater-6 Gallon
Feb 07, 2010 | Rinnai Vent Free Gas Heater/
Dec 11, 2009 | Water Heaters
97 people viewed this question
Usually answered in minutes!