Question about Goodman CLQ36AR49 Air Conditioner
I replaced my heat pump with a Goodman GSH 130601 inside and outside unit in May 2007. In July 2008 my compressor quit running. Serviceman said compressor was seized or locked and would have to replace. Next day they put a hard start unit on the compressor and it ran. Serviceman said he talked to Goodman and they told him they were having problems with their 5 ton compressors locking up. I was told by a friend, he is a refrigeration tech, the hard start unit is just a band-aid fix. He said I will likely have more compressor problems. I have a 10 year parts and compressor warranty from Goodman but with a $200.00+ service charges I don't want additional problems. Is the hard start unit just a quick fix and could I have more problems with a compressor that has already locked-up? My compressor always made a loud start-up noise from the day it was installed. Now the compressor is making a swishing sound, not from fan, and is even louder on start-up.
First and foremost ignore 90% of what anonymous posted. Goodman merged with Amana and make a very solid/quiet unit. The fact that the compressor was faulty is the fault of Copeland who made the compressor. New units do not require a hardstart, that is a bandaid to get more life out of an old compressor. The compressor should be replaced.
Posted on Oct 21, 2014
Goodman makes the cheapest unit on the market bar none. they are the absolute lowest end of the scale when buying a system. they are for that reason the best selling unit in the industry. so you should expect loud and clunky performance. expect only that they will perform, but dont even begin to expect them to perform quietly or smoothly. your warranty is only a year on these cheap pieces of equipment compared to a 5 or 10 year parts and labor warranty on trane and am standard equipment,so the labor will eat you alive on the cheap stuff. and when the expensive parts fail they will be really expensive.all compressors are now manufactured by about three compressor manufacturers, copeland tecumseh and bristol. so what ever brand you buy will have possibly the same compressor in it. all ac s in recent years have expansion valves that require a hard start kit. many cheap sluggo installers will not add the required hs kit even though they know it is needed and required by the manufacturer. so if the txv ( thermostatic expansion valve ) is a non pressure equalizing valve it has trouble starting against unequal pressure and voila , the compressor wont start. i have seen many a dumb+++ add a start kit to boost starting torque when the oem run capacitor is in fact weak or bad . if run cap is weak (test it) the start cap will temp fix. but you have not really fixed the problem if the run cap is bad eventually it will fail then no start again etc. despite the fact its a year old heres what you need to do. check filter for cleanliness. vacuum out drain for clean and clear drainage, run unit 15 minutes on a warm day , check run caps on fan outside and on compressor outside . they should be within 10 percent of rated mf values printed on side.feel suction line, cold? ok. not cold? call a pro for under charged or inefficient compressor. if cold then look at contactor points. they should be clean and golden colored. no char ,no gray or dark areas. a pro can tell with gages if charge is low or compressor is weak. as high pressure falls off and gets low ,suction pressure gets weak and rises. this would be a weak or bad compressor. as head ( high) pressure falls and suction pressure also falls this would be a case of low ref charge. you as a home owner can stick a cheap thermometor in the incoming and outgoing duct and expect to see a difference of 20 degrees . less equals low charge, or weak compressor,
Posted on Oct 12, 2008
Tell them you want a whole new outside system or a new compressor . Around here, the compressor change out should be around 5--$800.00 and the unit change out , around $400.00! OKLAHOMA.
Posted on Sep 07, 2008
Tips for a great answer:
Dec 21, 2015 | Air Conditioners
May 21, 2014 | Goodman 3 Ton 14 ee Goodan Heat Pump...
Feb 03, 2014 | Goodman Air Conditioners
Apr 12, 2013 | Bryant 462AJC021BA Air Conditioner
Jul 15, 2011 | Air Conditioners
Jan 27, 2011 | Air Conditioners
Jan 07, 2010 | Goodman Air Conditioners
Sep 19, 2009 | Goodman CLQ36AR49 Air Conditioner
Dec 20, 2008 | Goodman CLQ36AR49 Air Conditioner
4,836 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: