Question about Goodman Heating & Cooling
Posted by Anonymous on
Take a jumper wire and jump out the R and W terminals on the furnace. The heat should come on. If it does not, you have a bad board. A steady blink indicates no call for heat. You may have either a broken thermostat wire or a bad thermostat if unit fires when you jump it.
Posted on Mar 20, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 28, 2014 | Goodman Heating & Cooling
Jan 24, 2008 | Goodman GMS90703BXA Heater
Feb 05, 2014 | Goodman Manufacturing Goodman GPH1348H41...
Nov 15, 2011 | Goodman Heating & Cooling
Oct 02, 2011 | Goodman Heating & Cooling
Aug 29, 2009 | Goodman Heating & Cooling
Jun 06, 2009 | Goodman CKL42AR42 Air Conditioner
Nov 19, 2008 | Heating & Cooling
Oct 22, 2008 | Goodman GMS90703BXA Heater
Oct 20, 2008 | Goodman GMS90703BXA Heater
150 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: