Question about Solar 2-wire Pull Chain Light Switch For Ceiling Fan Lights
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
either one all it does is complete the circuit. only one wire is broken to open the circuit when you cut it on and off you just open and close the circuit with one wire.
Posted on Jul 29, 2009
You're correct. The dimmer switch was not made for that fan.
The Green is ground > so you're right there too. I assume other plugs nearby are working when dimmer is on. Check that to make sure.
By your description, I assume there is NOT another switch or dimmer that connects to same light. If so, you need a 3-way switch and the following instructions are void.
I suspect when you wired the new fan, that you saw the red and small black wires in the ceiling box. Did you connect the fan and light to those wires? If so, the following information will help you wire the switch.
Your incoming Hot line is probably the larger black wire that connects to Dimmer black >>> this wire will connect to either screw on the new switch
To test Hot wire for sure: Take out dimmer and mark wires for identification. Separate wires. Turn on power and test each wire to bare ground. Tape tester leads to wood sticks so hands are away from power. You'll be fine. Tester lights up on Hot wire.
Next: The smaller black and a red wires are a toss up.
Here's how I would proceed. Connect the black Hot to either screw on switch. Connect red wire to other screw. Put wire nut over small black. Turn on power. Flip switch. Check both lights and fan to see which works with red wire.
Next reverse the toss up wires. Put wire nut over red. Connect small black to switch. Check both lights and fan.
If red and small black control the light & fan, then connect them together on the same screw, and you're done.
If you want to control the fan and light separately, buy double switch, and then Hot connects to dark-colored screw on one side of switch, and red and small black connect to two different screws on opposite side of switch.
Posted on Oct 04, 2010
Testimonial: "Thanks That definitely helps..."
SOURCE: I have a 3 speed
Hello. Not realy familiar with those four in combination, but here's a link to some troubleshooting advice: http://www.ceiling-fans-n-more.com/ceiling-fan-pullchain-replacement-and-repair.php and a link to diagrams: http://www.hurontel.on.ca/~taitg/pages/cfan.html
Hope these help clear up you issue.
Posted on Mar 25, 2011
Tips for a great answer:
Nov 08, 2014 | Car Audio & Video
Oct 30, 2013 | Car Audio & Video
May 09, 2011 | Alpine Car Audio & Video
May 03, 2011 | 2002 Dodge Neon
Feb 20, 2011 | 2006 Nissan Altima
Dec 23, 2010 | Car Audio & Video
Dec 18, 2010 | 1996 Jeep Grand Cherokee
Oct 03, 2010 | Chrysler Fifth Avenue Cars & Trucks
Jun 14, 2009 | Alpine CDM-7854
Jun 03, 2009 | Pioneer DEH-P2000 CD Player
Apr 13, 2018 | Kohler Electrical Supplies
154 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: