Question about Heating & Cooling
Dear Scottness84, If you have the bill the last serviceman gave you, does it list that hardstart as part of what he did? Either way, the answer to your question is yes, it could cause your unit not to start. The first thint I would ask you to do is shut off the power to the outside unit. Set your thermostat to it's coldest point (just for now). Before you turn the breaker back on, remove the burned out hard start as it is not supposed to be needed. Turn the breaker on and listen. You should hear the fan start and see the blade turn up to speed. At the same time you should hear the compressor start. It will start out as a mechanical growl and then begin to quiet somewhat. If all you hear is a hum, then shut the breaker off as you either have a bad "Run Capacitor" or a locked up compressor. The "run capacitor is grey or silver in color and may appear swollen. Also, if you are able to get to it, make sure the wires are attached to all three terminals on the compressor itself. Many compressors have been condemned due to burned wires. I hope this helps. Sorry I posted in the wrong place at first
Posted on Mar 19, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 16, 2015 | Hotpoint Refrigerators
May 05, 2014 | Simpson MegaShot 3100 PSI Gas Powered...
Feb 28, 2012 | Keurig B60 Coffee Maker
May 29, 2011 | Friedrich Heating & Cooling
May 04, 2011 | Danby DDR586R Dehumidifier
Sep 21, 2010 | Amcor PLM-14000E Portable Air Conditioner
Aug 25, 2008 | Dometic Rooftop RV Air Conditioner
85 people viewed this question
Usually answered in minutes!