Question about Fahrenheat FBE15002 Baseboard Heater
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
nothing wrong w/ 10/3 @ 20A. use the red and black and don't use the white. dosent matter which is which (blk and red).
Posted on Mar 22, 2009
Is your fuse box and main power source large enough to handle the full load if all are turned on at the same time? Are you uses two pole breakers? you might only be feeding with 110 volt. This would prevent them from getting very hot.
Posted on Mar 08, 2009
If there is a 15 amp breaker on this circuit now. Then I would assume the the wire to this breaker is only capable of handling that size and NOTHING larger. There are to many variables. You need to know the maximum amp draw rating of the device. The wire size going back to the service entrance (fuse box). You will also need to know the total power draw of the service entrance to determine if the box can handle the total load. Are there any other branches off of this circuit? I suggest that you get advice from an electrician. If you overload the circuit, you may think everything is ok. But you can cause a major problem. I do not think that you want to take the chance of overloading a circuit. This can cause a fire and or death. Have this inspected by a professional. If you insist on doing it yourself.... contact your local building inspector for guidance.
Posted on Apr 26, 2009
Tips for a great answer:
Mar 15, 2014 | GE 20 Amp 1 In Double Pole Circuit Breaker...
Mar 10, 2014 | Electrical Supplies
Oct 28, 2012 | Raypak Spapak Electric Spa Heater -...
Sep 25, 2012 | Heating & Cooling
Jan 04, 2012 | Home
Sep 07, 2011 | Whirlpool Dryers
Dec 07, 2010 | Intermatic T104M 208-277Volt 40-amp Timer...
Jan 03, 2010 | Fahrenheat FBE15002 Baseboard Heater
465 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: