Question about American Standard Heating & Cooling
I would check the outdoor unit, Trane uses "Sump Heaters" on their compressors
and when one fails it will blow fuses at the disconnect or trip breakers.
The sump heater is a small metal pencil sized item at the bottom of the compressor
with something that looks like lamp cord going to it. Also when the start capacitor
fails it will exhibit this symptom. Look at the can shaped items inside the cover
If they are leaking, or bulged this may also be the problem.
(with the breakers off to everything including the inside unit to prevent shorting
These are the most common problems and the parts are less than 20 dollars each.
I service 155 trane units at my properties.
hope this helps.
Posted on Mar 19, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 14, 2017 | American Standard Heating & Cooling
Feb 03, 2016 | American Standard Heating & Cooling
Dec 21, 2015 | Heating & Cooling
May 18, 2014 | Trane American Standard Trane American...
Apr 24, 2014 | American Standard Heating & Cooling
Aug 27, 2012 | Heating & Cooling
Feb 26, 2010 | American Standard Heating & Cooling
Feb 26, 2010 | Heating & Cooling
Jul 02, 2009 | Heating & Cooling
Jun 11, 2009 | Heating & Cooling
180 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: