Question about MGE Galaxy 3000 UPS System
Try doing a restart procedure. Check pages from 35 to 37 in manual below. Disconnect connected devices. If there is overload because of a defective device connected, the first of the three leds at the bottom left hand corner will flash.
The UPS bypass switch may trip to test for the following reasons:
There is no AC power -LED 34 and LED 35 are flashing.
The battery has drained or is defective. LED 35 is flashing.
There is an internal fault (minor). LED 36 is flashing.
There is a short - The switch trips and the unit turns off. In this case the relay board is frequently location of the problem.
Here a picture showing the LED:
The unit also turns to test when the static switch is not closed (check also page 46 on manual). If the unit is starting up, try resetting to factory, by entering programming code 000 (see manual).
Here an online manual:
MGE Galaxy 3000
Posted on Mar 18, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 27, 2017 | Denon Audio Players & Recorders
Nov 05, 2012 | 2003 Pontiac Aztek
Aug 17, 2011 | Ovens
Feb 14, 2010 | Heating & Cooling
Mar 28, 2008 | Beko 24 in. D3421F Free-standing...
145 people viewed this question
Usually answered in minutes!