Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
The first thing I would check is the outdoor unit coil and see if it is restricted(dirty). If that is the case then you can wash it off with water(make sure you shut the power off to the unit first). If the outdoor coil is restricted and has little air flow thru it ,it can't get rid of the heat from the space and the compressor will draw over amperage and trip the breaker.
The next thing to check is if the outdoor fan is running. If the fan doesn't run it is the same as the restricted coil, it can't get rid of the heat from the coil. Check these things first then we can go from there! Thanks!!
Posted on Nov 24, 2009
Tips for a great answer:
Feb 16, 2015 | Universal Televison & Video
Jul 05, 2008 | Televison & Video
Dec 04, 2014 | Heating & Cooling
Sep 08, 2013 | Televison & Video
Dec 31, 2010 | Danby DPAC12031 Air Conditioner
Nov 22, 2009 | Heating & Cooling
Jul 07, 2009 | Washing Machines
Oct 20, 2017 | Heating & Cooling
62 people viewed this question
Usually answered in minutes!