Question about Coleman Propane Forced Air Heater w/Electronic Ignition (50,000-80,000 BTU)
IT could be the temp is too cold at night and the tank cannot make vapor ie gas, The liquied has to boil inside to make the gas you can get a heat blanket to warm your tank. Ask you gas suppier if they have one.
Posted on Mar 20, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 02, 2017 | Coleman Heating & Cooling
Dec 14, 2013 | Honeywell Programmable Thermostat Heater
Jan 06, 2013 | Heating & Cooling
Feb 10, 2011 | Coleman Heating & Cooling
On a call for heat, the 24 volt thermostat sends a signal to the control module. The control module will indicate a call for heat with a light on the control either blinking or remaing solid depending upon model. The inducer (exhaust) blower will purge all gasses from the furnace and pressurize a pressure switch. Once the pressure switch tells the module to continue, the electronic ignition will energize and send 120 volts to the igniter. The igniter will glow and you will be able to see it if viewed thru the small inspection port. Once the igniter gets hot enough, it sends a signal to the module opening up the gas valve (24 volts). Either a pilot will come on or the burner tube will ignite then spread the flame to all burners. Lastly a safety sensor will be looking for a certain temperature within a few seconds and the furnace will continue to operate and the room air blower will turn on in a minute or two.
What could go wrong? The unit will not run if there is no signal from the thermostat (bad thermostat or broken wire), the control module does not sense a signal from the thermostat (bad control), the inducer does not energize (bad motor), the pressure switch does not close (blocked vent piping, bad switch, plugged condensate hose), the igniter does not energize (bad control, bad igniter), the gas valve does not open or there is no gas (bad gas valve, broken wire, no gas), the pilot does not light (dirty pilot), the burner does not light (bad burner, plugged orifice, not enough combustion air), the flame does not spread to each burner (bad flame spreader, dirty flame spreader, more bad burners), the flame safety sensor does not detect flame (dirty or bad flame spreader, bad flame sensor, broken wire, bad control), or the room air blower does not energize (bad fan motor, bad control).
Oct 05, 2010 | Goodman GMS90703BXA Heater
Jan 23, 2010 | Heating & Cooling
Dec 26, 2009 | Coleman Heating & Cooling
Mar 31, 2009 | Coleman Propane Forced Air Heater...
Jan 17, 2009 | Coleman Propane Forced Air Heater...
Jan 06, 2009 | Heating & Cooling
May 15, 2014 | Coleman Propane Forced Air Heater...
157 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: