Question about Heating & Cooling
A thermocouple is used in keeping pilot lights lit in water heaters, boilers, furnaces. Opening gas valves in ovens. A thermocouple has a heavy copper wire leading into the pilot
flame, the pilot flame heats the upper 1/3 of the thermocouple
lead, generates up to 35 millivolts and energizes a coil to hold the gas
valve open; new furnaces do not have thermocouples, they use electronics to sense
Anyone trick there, just need to be patiente, first shut the gas off to the furnace, unthread the thermocouple from the gas valve and from the pilot assembly. Just reinstall it the same way to removed it. Just make sure when you re-light the furnace that the end of the thermocoupler is recieving a direct hit from the pilot flame.
A thermocouple is generic except for it's length. Thermocouples are made in different lengths. Measure the removed part or take the one you remove to any hardware store and replace it with an exact duplicate in length. The parts cost is very nominal.
New thermocouple packages will contain complete do-it-yourself installation instructions and pictures. The package also contains additional clips of various assortments. None may not even be needed.
Not all the parts contained in the package with the thermocouple will be needed. The packages contain an assortment of holding parts and clips that are generic and designed to fit a wide variety of applications.
Install new T-Couple into pilot assembly exactly as the existing one is installed. Element end must be placed exactly the same height as the exiting one. Re-install pilot assembly as found.
Gently thread nut end of T-Couple into gas control valve, starting threads by hand to insure threads will not cross thread and become damaged. Tighten nut snugly but do not overtighten. Just snugly until lightly bottoms out.
Be sure the pilot flame is all blue and no yellow. If any yellow or doubt pilot flame is correct or maybe dusty, clean it out. Blow out pilot flame and allow assembly to cool. Use can of computer keyboard canned air cleaner to blow out the entire assembly.
Re-light pilot and note the result. Test the pilot again note any changes. Also be sure the T-Couple is correctly installed in the pilot assembly. Only the tip of T-Couple or about top 1/3 should be heated. Must be glowing a bright cherry red color.
Hope this helps.
Posted on Mar 16, 2011
The connection to the gas valve is electronic, so proper contact is critical. disconnect and reconnect to finger tight, then EXACTLY one-quarter turn more with the proper wrench, no more, no less, if it wont stay lit, then you might need a new thermocoupler.
Posted on Mar 16, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 19, 2014 | Magic Chef Refrigerators
Oct 10, 2014 | Tools & Hardware - Others
Dec 19, 2013 | Ovens
Dec 18, 2012 | Magic Chef Ovens
Jan 07, 2010 | Ovens
Jul 15, 2009 | Magic Chef 31000 Gas Kitchen Range
Oct 24, 2008 | Montgomery Ward (223600UP) Heater
333 people viewed this question
Usually answered in minutes!