Question about Fujitsu 24C1 Air Conditioner
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
If your remote control have display but cannot transmit signal to the unit. Confirm first if the remote is really the problem, using your camera or cellphone camera as your eyes point the remote transmitter to your camera and "on" the remote. You should see light emits in your remote control, if no emitted light then the remote control is defective. But if there is a light the defect is in the unit receiver.
Check also if there is a reset or rst button in your remote control and reset it and try.
Check also if there are error codes in the unit, reset the unit by disconnecting the power supply in the unit for 10 sec. and "on" again and try.
The unit can be operate without remote control, use the manual button located in the unit.
If the remote control have no display replacement of remote is recommended.
Posted on Jan 16, 2009
If you contact Fujitsu in your country and you will be able to buy it straight from them, if they are still available. Now I have to warn you as a Fujitsu warrenty agent they are very very expensive.
I would prolly recommend getting a universal remote. ALOT cheaper
Posted on Jan 23, 2009
After changing the batteries you have to depress the RST button and if the remote has the abcd slide switch ensure it is set to A.
Posted on Jul 15, 2010
Tips for a great answer:
Aug 02, 2015 | Fujitsu Heating & Cooling
Jan 18, 2015 | Fujitsu Heating & Cooling
Oct 10, 2013 | Fujitsu Heating & Cooling
Sep 11, 2010 | Fujitsu (FPCRC04AR) Remote Control
Jun 29, 2010 | Fujitsu 18C1 Air Conditioner
Aug 20, 2009 | Heating & Cooling
Jul 07, 2009 | Heating & Cooling
Jan 15, 2009 | Heating & Cooling
745 people viewed this question
Usually answered in minutes!