Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
First off, I dont think you caused this problem by vacuuming the unit. It is possible that you did not leave much time before restarts but you then said you tried leaving it off for 5 minutes which should be adequate enough. f you let the unit set for a couple of hours before a restart that should be enough time for the compressor to cool down to ambient temp. I would then try restarting the unit, if it works leave it on for a while and make sure it is producing enough cooling. If there is no change in the situation I would suggest that it would need to come back out of the housing and check that the compressor is receiving voltage to it. It is possible a start capacitor or relay is the cause of the problem. If it started first time I would suggest it is worth having it checked by a professional as it could be the charge or the starting devices. First off though let it completely cool down and try again. Hope this is of some help.
Posted on Sep 15, 2007
SOURCE: Fan runs, but when compressor
The compressor has a safety switch under the cover where the wires connect to it. That's what is kicking out. You should check the capacitor connected to the start winding. Check the wires where they connect to the compressor. A burnt off wire for the run terminal will cause these symptoms. If that's all good, it's being fed correctly on all 3 terminals, the compressor has stalled and will probably never start again. You can try a "hard start" kit, but not on a Scroll compressor (read the label). They aren't designed to survive that.
Posted on Jul 27, 2008
SOURCE: Amana Gas furnace, Air Command
Buy a new ignitor here; The Ignitor Store. Or talk an Amana dealer/Contractor to sell you one. They can range from 15 to 35 bucks! Depending on their mark-up. Give them your model number, and or ignitor part number. Their simple to change out, good luck, please contact if you have any questions.
Posted on Dec 02, 2008
SOURCE: Slow gas on Carrier 8000 58TUA?
Saw this happen one other time where the regulator at the outdoors gas meter was faulty and not supply the correct gas pressure. You may need to have the gas company come out and check the pressure at the meter. Also, check to make sure no other gas appliances are running..ie..water heater, gas logs, stove, etc. and then start up the furnace and see if it will start up properly. This would also indicate a problem at the gas meter...ie..gas pressure.
Posted on Dec 21, 2008
Try cleaning the flame sensor. It is located right besides the last burner. Looks like a thick piece of wire. Take steel wool and gently remove the carbon that has built up. Should only take 4 or 5 strokes. Let me know how it goes after that. ken
Posted on Dec 23, 2008
Tips for a great answer:
Mar 26, 2017 | Water Water Heaters
Feb 22, 2017 | Water Water Heaters
Feb 23, 2016 | Water Water Heaters
Sep 08, 2015 | Water Heaters
Dec 04, 2013 | Water Water Heaters
Dec 13, 2012 | Water Heaters
Jan 02, 2011 | Sunbeam Heating & Cooling
May 24, 2010 | Rheem 40 Gallon FVR NATGAS Low WATER...
Jun 29, 2009 | Kitchen Ranges
217 people viewed this question
Usually answered in minutes!