Question about Goodman Heating & Cooling
Hello, if the burners do not fire at all there could be a few reasons, the igniter could be bad, the burners could be dirty not allowing gas to flow, the pressure switch could be open. There should be a led light code on the control board that will tell you where to look. Begin by checking the hose between the inducer motor and pressure switch, it could be loose, kinked, or have a obstruction in it such as water not allowing the switch to close, also check the flue pipe for any obstructions. If the switch checks out good than the igniter should be inspected for any cracks or white spots, this is a sighn that the igniter is weak and should be replaced. If the igniter is good then clean the burners.
Posted on Mar 15, 2011
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Nov 08, 2016 | Heating & Cooling
Mar 07, 2015 | Heating & Cooling
Sep 19, 2011 | Heating & Cooling
Sep 01, 2010 | Heating & Cooling
Nov 24, 2008 | Goodman GMS90703BXA Heater
Nov 10, 2008 | Goodman GMS90703BXA Heater
62 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: