Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Hopefully there are markings on the old t-stat as to what terminal is what.
on the honeywell 8000 use the heat pump labeling and then the standard wiring would be
There should not be a bare wire, it probably just has the insulation stripped back way too far.
You should probably open the furnace and compare the terminal label in the furnace to the wire color. normally yellow and blue pass through the furnace and are wire nutted to wires going to the outdoor unit. In the furnace the white wire will connect to the w or w1 terminal. also, you will need to set the Honeywell stat to have the following parameters.
other parameters that I did not specify, you may read the manual and make your own decision but I recommend factory settings for the other parameters
Posted on Jun 18, 2008
There is a sensor that shuts the compressor down when the freon (refrigerant) is low. The tech probably "shorted" out this sensor. If the unit went on when he did this, the charge is low.
Posted on Jul 08, 2008
Every thing the same except take your blue wire and replace the yellow for it. So when you hook it to t-stat goes like this
Red to R
White to W
Green to G
Blue to Y
Posted on Jan 16, 2009
Hook up o to o/b, then in the installation programming set the change over valve to energize in cool. Then hook up w to aux. Good luck.
Posted on Jan 21, 2009
Your old stat is wired for a traditional thermostat and not a communication stat like the new infinity you have. There is a module plug on the furnace board that will need to be connected to the new thermostat for it to work. The wires that are wired now are from a terminal strip inside the furnace. Please contact your local Carrier dealer. They may be able to get that harness for you
Posted on Jan 10, 2010
Tips for a great answer:
Dec 20, 2014 | Honeywell Heating & Cooling
Nov 10, 2010 | Hunter Heating & Cooling
Oct 19, 2010 | Honeywell Programmable Thermostat Heater
May 21, 2010 | Carrier 38BRC048 Air Conditioner
Nov 01, 2009 | Honeywell Electronic Programmable...
Aug 12, 2009 | Honeywell Electronic Programmable...
Jan 05, 2009 | Honeywell Electronic Programmable...
Dec 06, 2007 | Heating & Cooling
268 people viewed this question
Usually answered in minutes!