Question about Carrier 38CKC036 Air Conditioner
My fan motor just humms and my compressor just clicks does it sound like the capacitor the blower in the furnace stays running
Yes dual feed capacitor in the condensor sounds bad. common to one side and outlet to compressor on the other and outlet to the fan on the third set of terminals. it should test bad but look carefully at it, it may be bloated up like a dead fish and easy to observe if you look at it closely. if bloated bad, worth a try anyway, cheap part ,usually under 40 bucks for most. label wires and reoplace wire for wire exactly with exact voltage and mf ratings. usually a motor shop has em. good luck.
Posted on Dec 07, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 12, 2015 | Coleman Heating & Cooling
Nov 16, 2012 | Rheem Prestige 14 Series 2.0 ton 14 SEER...
Nov 08, 2011 | Intertherm P3RA-048K Air Conditioner
Jun 11, 2011 | Carrier 38CKC036 Air Conditioner
Oct 29, 2009 | Goodman CKL24AR24 Air Conditioner
May 30, 2009 | Bryant 463AAC005BA Air Conditioner
Sep 15, 2008 | Ruud UBHC Air Conditioner
Jun 23, 2008 | Dometic Rooftop RV Air Conditioner
Jun 25, 2014 | Carrier 38CKC036 Air Conditioner
Jun 13, 2014 | Carrier 38CKC036 Air Conditioner
114 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: