Question about Raypak Rp2100 Pool & Spa Heater Lonox 407k Btu Natural Gas Polymer Header Digital Rp407aenc
Hi Check the gas valve ,it is open .The GVO indicates that the gas valve is open. Please get back to us if you have further query else please accept the suggestion. Thank you for contacting fixya.com
Check the gas valve ,it is open .The GVO indicates that the gas valve is open.
Please get back to us if you have further query else please accept the suggestion.
Thank you for contacting fixya.com
Posted on Mar 19, 2011
GVO means the units gas valve is open or at least the circuit is. You will need to look at two things:
First, is the valve hooked up properly? Pull the leads from the valve and check incoming voltage during the ignition sequence. If it is present then the problem is the valve itself.
Second, assuming power is getting to the valve during ignition sequence, hook a manometer to the pilot port and look for pilot gas pressure during the ignition sequence. If none is present replace the valve.
Posted on Mar 16, 2011
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
spk I think means spark for ignition and plt means pilot so i assume the heater tried to light but the pilot light is not staying on. could be dirtly contact on the ignition spark plug or dirty pilot flame need to be cleaned and the unit serviced.
i hope this was useful.
May 28, 2014 | Raypak RP2100 DIGITAL POOL HEATER R265
Aug 03, 2010 | Raypak Free Hydraulic Lift Gate Delivery -...
Mar 29, 2009 | Raypak Rp2100 Pool & Spa Heater Lonox 407k...
Dec 26, 2008 | Raypak Pool Heater Covers for Teledyne &...
823 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: