Question about Heating & Cooling
Probably not the switch, MUCH more common is the sensing tube. This is the copper tube that goes into the gas control valve, and the other end is TOUCHED by the pilot light flame.
(The flame heats this tube and then this allows the pilot to remain on. The thinking is if the pilot were to go out, it is important to stop the flow of gas....)
These sensing tubes are readily available, but different across brands, so be sure to get the correct one for your unit. Easy swap out, do not kink the tubing and put the sensing end in the same position as the old one, relative to the pilot flame....
The start proceedure requires that you override the tube, light the pilot light, and continue to hold the override for xxx amount of seconds. How long differs, I observe the flame and then slowly let off the override, ready to re press if the flame were to lessen or go out.....
Posted on Mar 11, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 10, 2016 | Robertshaw 720-007 universal gas valve for...
Jan 14, 2015 | Heating & Cooling
Dec 09, 2013 | Heating & Cooling
Sep 15, 2011 | Dayton Gas Furnace Heater
Nov 12, 2009 | Heating & Cooling
Oct 20, 2009 | Heating & Cooling
Aug 08, 2009 | Teledyne Laars Laars Lite 2 Pool Heater...
Apr 15, 2009 | Heating & Cooling
Jan 06, 2009 | Heating & Cooling
Aug 21, 2017 | Heating & Cooling
57 people viewed this question
Usually answered in minutes!