Question about Heating & Cooling
Hi, W/D here.
A humming noise can indicate that the motor isn't getting the necessary starting kick to start up. This extra starting kick is supplied by the start capacitor.
This can also be a problem with the motor proper. The cheapest thing to try is to replace the start capacitor. It is a can looking device that will be located near the motor, and connected to the motor by two brown wires. Trip your breaker outside for the A/C, and trip the service disconnect in the A/C cabinet. Use insulated tools to remove the wires from the capacitor, and do not touch the terminals with bare fingers as a shock could result, even after the wires are disconnected.
Locate a local appliance parts supply company, and take your old capacitor with you to get a replacement. Capacitors and motors are matched, so it is important to get a replacement with the proper rating. Reconnect the new capacitor and try it out.
A capacitor will cost in the less than, but close to $20 range, and is worthy of a try, and will probably fix your problem. If it is the motor itself, a motor and matched capacitor will cost you around $110, or less, depending on the horsepower of the motor. Again, any local appliance parts supply house, or A/C supply will have the necessary parts, and it is not a hard job to do.
Best regards, --W/D--
Posted on Mar 11, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 19, 2016 | Heating & Cooling
Nov 13, 2014 | Heating & Cooling
Jan 03, 2011 | Heating & Cooling
Jun 23, 2010 | Maytag M7Y12F2A Air Conditioner
Apr 24, 2009 | Ruud Central System Air Conditioner
Jan 22, 2009 | Heating & Cooling
Dec 28, 2008 | Ruud UAMB Air Conditioner
Sep 01, 2008 | Bryant Heating & Cooling
Jul 11, 2008 | Coleman Heating & Cooling
43 people viewed this question
Usually answered in minutes!