Question about Dyna-Glo D-E37 Wall Mounted Panel Heater
I am assuming you are talking about a type K ( Chromel, Alumel ) type Thermocouple. A junction of these two alloys ( welded together by capacitance discharge) produces 41 micro volts per degree Celsius. As the flame from a perfect air/gas mix produces a flame around 1900 C (propane), and 2000 C (natural gas) . You can simply multiply.
41uV X 1900 = 779mV For propane
41uV X 2000 = 822mV For natural gas
This should give you a pretty good Idea of what you should be looking for. If you are using a standard volt meter to obtain a reading. Touching the leads of the probe to the leads of the meter in affect creates two more thermocouples unintentionally. This will alter your reading only slightly due to the fact that the temperature will be at relatively negligible at the contact points.
Allowing for this distortion you should expect a reading +/- 50mV either way. I hope you find this information helpful. Please take the time to rate this fixya for me. To compensate me for the 4 years of my life I spent cramming weird stuff like this in my head in college and the 5 minutes I spent typing this out for you for free. LOL If you ever need my help select me as one of your experts and I will help you for free.
Posted on Jul 28, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 10, 2016 | Heating & Cooling
Dec 28, 2014 | Heating & Cooling
Feb 04, 2014 | Goodman GMS90703BXA Heater
Nov 02, 2011 | Dayton Gas Furnace Heater
Nov 01, 2010 | Blue Rhino ES200209 Open Flame Gas Patio...
Dec 21, 2009 | Endless Summer UniFlame (GWU501E) Open...
Dec 09, 2009 | Desa International Heating & Cooling
Oct 03, 2009 | Heating & Cooling
Dec 18, 2008 | Heating & Cooling
Dec 04, 2007 | Heating & Cooling
311 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: