Question about Dometic Rooftop RV Air Conditioner
The AC (Duo-Therm Model 57915.622) in my RV has been working great until today. All of a sudden, the compressor would sound like it was kicking on, but then just hum for a few seconds, and then kick off. When this occurred, I can smell a slight electrical smell coming out of the AC vents in the ceiling. About 10 seconds after the compressor kicks off, it tries to kick on again and repeat the same cycle.
Sounds like your start capacitor may have gone bad. If you remove the shroud, there should be an access panel for the electronics. In there, you'll see one (or two) cylindrical parts with wires coming out the top. If one of them shows signs of something coming out of it, it's probably your start capacitor and it needs to be replaced.
You can view the installation/service manual for DuoTherms here at Bryant RV.com (it's a 3MB PDF file, so download with care). Look on page 28 for info on the capacitors.
Posted on Oct 13, 2008
Something has gone wrong and needs to be repaired. It's an electrical problem. The more you smell it, the more stuff is getting burnt. Take it apart and look inside it. Then restart it. The burning stuff will lead you to the bad part.
Posted on Jul 27, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 01, 2013 | Dometic Rooftop RV Air Conditioner
Nov 15, 2009 | Ovens
Sep 28, 2009 | Heating & Cooling
Sep 20, 2009 | Dometic Rooftop RV Air Conditioner
Jun 15, 2009 | Dometic Rooftop RV Air Conditioner
Jun 08, 2009 | Dometic Rooftop RV Air Conditioner
Nov 17, 2008 | Dometic Rooftop RV Air Conditioner
Apr 16, 2008 | Dometic Rooftop RV Air Conditioner
652 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: