Question about LG Electronic Window Air Conditioner
Not sure if this is what you're looking for, but if it might help... I just posted this on a similar issue (water buildup in the front of the unit and/or a rattling noise when the fan is running - sounds like it's running through water and it's spitting water out of the vent). I'm guessing that it's designed similarly to other LG units...
If the unit has been working fine for a long time and then you suddenly have this issue, the angle you have the unit set at is probably fine, but you probably have a blockage of dirt/mud/sludge/whatever that is keeping it from draining properly. Here's what you have to do...
For safety... turn the unit OFF and UNPLUG IT.
Open the front gate and remove the air filter. Next, remove the entire front gate from the unit (probably at least one screw to remove first - mine was in the middle, just under wher the bottom of the air filter sits). With the gate removed you should have access to locate your blockage problem.
There is a hole that allows the water to drain from the front of the unit (the part that is inside your house) to the back of the unit (the part that hangs outside your house) and eventually out of a drain hole in the rear. Chances are that this hole is clogged. So, when the water fills up in the front drip tray it has no access to drain to the back. Consequently, the water builds up in the fan area which causes the rattling noise and the water being picked up by the fan and blown out of the vent. If left too long, it will overflow the front drip tray and make a mess in your house.
On my unit, the hole was on the far left side (if your are in your house and facing the AC unit) of the drip tray. You can use a piece of coathanger wire, or some other long thin instrument to push the blockage through to the rear. Once this pathway from the front of the unit to the back of the unit is clear, your problem should be solved. You will probably still get the sound and water sputter out of the front for a little while until the water that is in the fan area drains/dries out, but it should return to normal soon.
It is probably best to actually remove the unit from the window and take the cover off of it and really clean it out, but that is obviously a much more involved task. If you have a hose, that's fine and will help. Water won't hurt the unit - just keep it away from the electronics (the controls/display/cord). You should also be carful not to bend any of the tiny metal fins... that's just as bad as (actually worse than) being blocked by dirt/dust. And obviously, allow the unit to dry before you put the cover back on and put it back in your window and plug it in to run it. If you are willing to put in the extra time and effort, you can do a more thorough cleaning job, which would help to prevent the problem from happening again too soon. There's no way to prevent dirt/dust from building up in the unit. Once water/moisture is added to the mix, you're dealing with mud/sludge, which is going to eventually block that small drain path. The only solution is to clean it out once in a while.
I figured this out the hard way. I took the thing out of the window cleaned it (not as thoroughly as I thought) and put it back in and then did it all again. The third time I actually found the hole that was blocked. If it hadn't been such a pain taking it all apart and cleaning it the first two times I would have laughed at myself for missing it.
Good luck! Hope this helps!
Posted on Jul 27, 2008
I have a lg l8010er and here is how i did it
inserting bbq skewer
and moving it in and out a couple of times and all done took me 15 mins to find the hole but i found it!
Posted on Sep 07, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 13, 2014 | GE 24000 Btu Room Air Conditioner EnerStar...
Aug 31, 2013 | Frigidaire FAC126P1 wall/window Air...
Aug 19, 2010 | LG LWHD1200FR Wall/Window Air Conditioner
May 16, 2010 | LG LM-2430C2L Cool Mini Split Air...
Feb 03, 2010 | LG Electronic Window Air Conditioner
Jan 19, 2010 | LG LM-2430C2L Cool Mini Split Air...
Oct 25, 2009 | LG Heat cool Window Air Conditioner
Jun 21, 2009 | LG Electronic Window Air Conditioner
Mar 25, 2009 | LG LS-L1210CL Mini Split Air Conditioner
1,317 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: