Question about Air Conditioners
The compressor has a safety switch under the cover where the wires connect to it. That's what is kicking out. You should check the capacitor connected to the start winding. Check the wires where they connect to the compressor. A burnt off wire for the run terminal will cause these symptoms. If that's all good, it's being fed correctly on all 3 terminals, the compressor has stalled and will probably never start again. You can try a "hard start" kit, but not on a Scroll compressor (read the label). They aren't designed to survive that.
Posted on Jul 27, 2008
Tips for a great answer:
Sep 11, 2013 | Dometic Rooftop RV Air Conditioner
Aug 17, 2013 | Air Conditioners
Sep 23, 2012 | Dometic Rooftop RV Air Conditioner
Aug 01, 2011 | Air Conditioners
Jun 29, 2011 | Air Conditioners
Jun 22, 2011 | Goodman CKL36AR36 Air Conditioner
Jun 15, 2011 | Weather King 10AJA3601AH Air Conditioner
Aug 04, 2009 | Amana PTH123B25AJ Heat Pump Air...
Jun 22, 2008 | Coleman Mach III Air Conditioner
Jun 16, 2008 | Coleman Mach 15 Air Conditioner
229 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: