Question about Heating & Cooling
The compressor has a safety switch under the cover where the wires connect to it. That's what is kicking out. You should check the capacitor connected to the start winding. Check the wires where they connect to the compressor. A burnt off wire for the run terminal will cause these symptoms. If that's all good, it's being fed correctly on all 3 terminals, the compressor has stalled and will probably never start again. You can try a "hard start" kit, but not on a Scroll compressor (read the label). They aren't designed to survive that.
Posted on Jul 27, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 11, 2013 | Dometic Rooftop RV Air Conditioner
Aug 17, 2013 | Heating & Cooling
Sep 23, 2012 | Dometic Rooftop RV Air Conditioner
Aug 01, 2011 | Heating & Cooling
Jun 29, 2011 | Heating & Cooling
Jun 22, 2011 | Goodman CKL36AR36 Air Conditioner
Jun 15, 2011 | Weather King 10AJA3601AH Air Conditioner
Aug 04, 2009 | Amana PTH123B25AJ Heat Pump Air...
Jun 22, 2008 | Coleman Mach III Air Conditioner
Jun 16, 2008 | Coleman Mach 15 Air Conditioner
229 people viewed this question
Usually answered in minutes!