Question about Heating & Cooling
The compressor has a safety switch under the cover where the wires connect to it. That's what is kicking out. You should check the capacitor connected to the start winding. Check the wires where they connect to the compressor. A burnt off wire for the run terminal will cause these symptoms. If that's all good, it's being fed correctly on all 3 terminals, the compressor has stalled and will probably never start again. You can try a "hard start" kit, but not on a Scroll compressor (read the label). They aren't designed to survive that.
Posted on Jul 27, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 05, 2014 | Samsung RSA1SHPN American Platinum Inox...
Apr 30, 2014 | Heating & Cooling
Apr 23, 2017 | Heating & Cooling
Mar 24, 2012 | General Electric APE08AK Portable Air...
Aug 29, 2011 | Amana SXD524VW Side by Side Refrigerator
Mar 23, 2011 | Refrigerators
Mar 10, 2011 | Amana Refrigerators
Mar 28, 2009 | Maytag MBB2254G Bottom Freezer...
Jun 22, 2008 | Coleman Mach III Air Conditioner
Jun 16, 2008 | Coleman Mach 15 Air Conditioner
231 people viewed this question
Usually answered in minutes!