Question about Coleman Mach III Air Conditioner
Wall thermastat set on correct settings fan operates compressor trys to to engage draws to much currant throwing breakers. has been suggested that the start capacitor could be faulty.
Good chance , just double check you have proper voltage going to it first.
Posted on Aug 16, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 07, 2017 | Heating & Cooling
Jan 04, 2017 | Heating & Cooling
Jan 03, 2017 | Royal Heating & Cooling
Jan 02, 2017 | Heating & Cooling
Dec 30, 2016 | Heating & Cooling
Dec 18, 2016 | Heating & Cooling
Oct 12, 2014 | Heating & Cooling
Aug 12, 2014 | Heating & Cooling
Jun 29, 2014 | Heating & Cooling
Jan 01, 2014 | Williams (5009622) Ceramic Gas Wall...
74 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: