Question about Ventamatic Direct Drive Whole House Fan With Univer
The shutters barely open on low speed.. They open most of the time on high speed but after awhile they close even though the fan seems to still be running. Thanks
The shutters should be gravity closed, which means they are counter weighted just enough to close with no air flow... when the fan starts, it will create a slight pressure differential across the shutters - when that pressure overcomes the counter weight, the shutters should open... I assume you open windows and/or doors when the fan runs...
I would check for the following items: a) (unlikely) check to see if the counter weight is adjustable, if so, it may be slipping and needs reset.. I think this is unlikely as I think most shutters do not have adjustable counter weights -- check last)
b) check your attic vents to the outside -- the air being blown into the attic must escape to the outside world, otherwise it will build up pressure and the airflow will drop or stop altogether -- this sounds like what is occurring, at slow speeds, there is insufficient airflow to open the dampers, at high speeds, they open long enough for the pressure to build up and then they close as the air flow diminishes
c) have you replaced windows, caulked up windows, made any modifications to reduce the flow of air into the living areas -- air must enter the house just as air must leave the attic (assumes you don't open windows or doors)
d) if you have a fireplace, check to make sure some animal or other hasn't plugged up the chimney -- if the house is tight, the attic fan will pull air from the chimney unless it is blocked
hope this helps...
Posted on Jul 27, 2008
Tips for a great answer:
Jun 19, 2013 | Fans
Jul 27, 2012 | Hampton Bay 24002 Ceiling Fan
Jul 01, 2011 | Fans
Sep 07, 2010 | Emerson Fans CF705AW 52" Northwind Ceiling
Aug 22, 2010 | Lakewood HV 18-c Floor / Box Fan
Jun 06, 2010 | Cool Attic 3011 Duct Window Mount Fan
Mar 26, 2010 | Hampton Bay 24002 Ceiling Fan
Aug 18, 2009 | Hampton Bay 24002 Ceiling Fan
Jul 27, 2009 | Hampton Bay AC414-LRU 52'' Kemper...
Apr 21, 2009 | Hampton Bay 24002 Ceiling Fan
185 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: