Question about Heating & Cooling
This is not an air conditioner but a fan forced heater. The control unit has died and a replacement is over $170.00 !! It's going to be recycled.
Posted on Jul 24, 2008
The control unit can be repaired. Usual problem is that the brown glue on the circuit board has absorbed moisture and corroded components. Remove glue and clean board. Then replace corroded components - usually a number of resistors. The power triacs are usually ok.
Posted on Mar 25, 2010
My display is working but very dim as compared to when it used to work properlly. My unit is a Quasar True Trach 4 System manufactured in the early 80's. Paid a lot of money for it then and it has some very nice features,,,
Posted on Apr 19, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 07, 2012 | Hayward H-series Electronic Gas Pool...
Aug 27, 2008 | Quasar Heating & Cooling
Jul 31, 2011 | Heating & Cooling
Is it an electronic with a digital readout and the readout is blank? If so, double check the toggle switch on the outside of the chassis on the right, looking at the front of the heater, is on. If it is and it is still dead confirm you have power up to the switch and then to the transformer inside the heater on the upper right sidewall. If you have power to the transformer then replace it; your problem would be the transformer secondary is dead therefore the heater is to. If you do not have power to the transformer but do to the switch replace the switch.
If you do not have a digital display please post a comment to that effect and include your unit's model number for further assistance.
If this answer does not fix your problem, please comment with additional details prior to rating the answer. You may also contact me thru our website at www.arrowpools.net. Positive feedback is appreciated once your problem is solved!
Jun 26, 2011 | Raypak 2100 Pool Heater Gas 266000 BTU'...
Jun 20, 2010 | Heating & Cooling
Apr 30, 2010 | Cozy Enclosed Front Console Heater 20,000...
Oct 05, 2009 | Heating & Cooling
Jul 27, 2009 | Heating & Cooling
Jun 06, 2009 | Sunbeam Heating & Cooling
Jun 03, 2009 | Heating & Cooling
704 people viewed this question
Usually answered in minutes!