Question about Heating & Cooling
Frost is caused by the refrigerant pressure being too low on the low pressure side of the system. That is, the compressor has more ability than the cold coil is using up. This can be caused by insufficient air flow over the cold coil or a shortage of refrigerant.
Insufficient air flow can be caused by a dirty coil, filter, or blower wheel, or collapsed ducts, to name a few. It is most likely that some of the refrigerant has escaped and the leak needs to be repaired and the refrigerant topped up to the right amount. You'll need to use the proper gauges, a good thermometer, and read the chart that is glued inside the access door on the condenser, or...check for any available repairs that are free because of your warranty.
I did know of a Sears 5,000 BTU window air that was simply designed wrong, but that was many many years ago.
Posted on Jul 22, 2008
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 26, 2015 | Heating & Cooling
Aug 01, 2014 | Maytag Heating & Cooling
May 26, 2014 | Haier Heating & Cooling
Sep 21, 2011 | Ruud Matching Split Air Conditioner
Sep 03, 2011 | Comfort-Aire Heating & Cooling
Feb 27, 2011 | Dometic Heating & Cooling
Jul 20, 2010 | Whirlwind FH-778 Air Conditioner
Jun 14, 2008 | Heating & Cooling
May 09, 2008 | Samsung AS18A6RB Air Conditioner
Jan 18, 2006 | Fedders A7DH65B2A Dehumidifier
Apr 21, 2018 | LG Heating & Cooling
137 people viewed this question
Usually answered in minutes!