Question about Heating & Cooling
The evaporator coil that is low pressure and low temperature needs an adequate supply of heat to absorb from air passing over the fins or a thin dusting of frost will begin to form further insulating the coil from the passing air and causing more ice to form. First you have to get rid of all the ice by allowing the coil to thaw you can use a heat gun or hairdryer or lamp to speed the thawing but the fins and copper tubing are thin and easily damaged so don't use tools on the coil to remove ice. After thawed the coil needs to be cleaned with an indoor evaporator cleaner ( I also use a small shopvac and nylon brush) Then be sure that the filter is clean and the blower is functioning properly then if the suction line is still frosting you will have to verify that the size of the outdoor section is not over sized in relation to the evaporator coil and that the system is charged to meet the compressors manufactures specifications.
Posted on Jul 21, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 30, 2014 | Kenmore 75184 Air Conditioner
Apr 22, 2014 | Frigidaire FAM157S1A Air Conditioner
Jun 19, 2012 | LG Heating & Cooling
Dec 04, 2009 | Amana PTH153B50AJ Heat Pump Air...
Sep 22, 2009 | Carrier Heating & Cooling
Sep 05, 2009 | Carrier 38CKC042 Air Conditioner
Aug 30, 2009 | Goodman CLJ30AR32 Air Conditioner
Aug 15, 2009 | Heating & Cooling
Apr 18, 2009 | Hunter 30124 Air Conditioner
247 people viewed this question
Usually answered in minutes!